You can help by commenting or suggesting your edit directly into the transcript. We'll review any changes before posting them. All comments are completely anonymous. For any comments that need a reply, consider emailing email@example.com.
We are experiencing playback issues from our video hosting provider. Please check back shortly.
1:47Connecting to Legacy CompactLogix
1:32Connecting to Legacy ControlLogix
1:29Connecting to ControlLogix v21+
1:24Connecting to MicroLogix
1:21Connecting to PLC5
1:23Connecting to SLC
4:16An ENBT Example
3:44A DH+ Example
Take topic challenge
Connecting to SLC
Learn how to connect to Allen-Bradley SLC (5/05 and 5/04) devices. Because these PLCs do not have a native ethernet connection, another device like an Net ENI or an ENBT needs to be used to connect.
Video recorded using: Ignition 7.9
Transcript(open in window)
[00:00] Let's take a look at how we would connect Ignition to an Allen-Bradley SLC device. First we want to log in to the Configuration section of the gateway webpage, and scroll down and go to the Devices page under OPC-UA SERVER, and click on the Create new Device link. We then want to select the Allen-Bradley SLC driver. This driver can connect to a SLC 505 through Ethernet, or a a SLC 504 through something like a NET-ENI module. We can then scroll down to the bottom of the page and hit the Next button. We then want to configure a connection, like giving it a Name. And a Hostname, which is the IP address of the device. In my case, it's 10.20.4.51. And then we hit the Create New Device button at the bottom. It will then browse the device for any tags, and connect to it. Once it has successfully connected, we can scroll down and view our tags in the Quick Client under OPC CONNECTIONS. We can expand these folders, find our device, and you'll see all the tags in the device by expanding any of the folders here.